NFPA 1403 and F.A.C. 69
Structural Evaluation Requirements
69A-37.404 Requirements for Live Fire Training
States in part “(18)(a) The 2002 edition of the National Fire Protection Association, Inc., Publication 1403, “Standard on Live Fire Training Evolutions,” is hereby adopted and incorporated by reference…”
NFPA 1403-2002 requires
18.104.22.168 The structural integrity of the building shall be evaluated and documented annually by a licensed professional engineer with burn building experience and expertise.
MELISSA AND BYRON, SINCE THIS LINK IS NO LONGER AVAILABLE, SINCE THEY REVISED THEIR WEBSITE, I AM GOING TO DELETE THIS ENTIRE NOTE, OKAY?
NOTE: For those who oversee…firefighting training centers, See the article >>>“Engineer: NFPA Training-Center Inspections Mandated, Not Optional“
22.214.171.124 Part of the burn building evaluation shall include, once every five years, the removal and reinstallation of a representative area of thermal linings (if any) to inspect the hidden conditions behind the linings.
126.96.36.199 The engineer shall core solid structural concrete slabs and walls that have been exposed to temperatures in excess of 149°C (300°F) to check for hidden Typical Live Fire Training Facilities – NFPA Image 3delamination and to test comprehensive strength once every 10 years for conventional (Portland) concrete and every three years for refractory (calcium aluminate) concrete.
188.8.131.52 Where the burn building damage is severe enough to affect the safety of the students, training shall not be permitted.
Are you in compliance?
For more information contact:
Byron Evetts, P.E, Fire Fighter,
USAR Structures Specialist and NAFI Fire Investigator.